Contract Type: BMS
Developer: Raine and Horne
Location: Neon House, Level 6, 8/10 Hobart Pl, Canberra ACT 2600
The existing BMS was an old system that had become outdated, had some inherent control issues, did not provide the full functionality that the building owners now require and relied upon elderly pneumatic control hardware which had become difficult to maintain. There was also a drive to achieve energy savings by more effective control of the HVAC systems.
The biggest challenge was achieving effective control of the dual duct heating system. The consultant engaged by the building owner had specified a control strategy to control the dual duct system as a VAV system. This proved ineffective and a new control strategy was developed and implemented by us which has proved to be effective and efficient.
Our scope entailed a Full BMS cut-over including replacement of old pneumatic control hardware and control of a dual duct full building HVAC system. We were able to develop a solution using our Optergy platform, Alerton DDCs, installation of new Belimo 24v control actuators and ABB variable speed drives (VSDs).
We were able to develop a control strategy to effectively operate the dual duct system including reducing fan speeds where appropriate and zoning the areas within the building for more efficient after hours operation. We were also able to facilitate after hours billing which enables the owner to recoup the cost of operating the building outside of the tenants contracted hours.